EN 301 489-1 V1.8.1(2008-04)
EN 301 489-3 V1.4.1(2002-08)
EN 300 440-1 V1.5.1(2009-03)
EN 300 440-2 V1.3.1(2009-03)
Power source: 100-240V/AC
Power frequency: 50/60Hz
Transmission power: <0.3mW
Working temperature: -15°C~+70°C
Protection level: IP20,Class II
Installation sit: indoors, ceiling mounting
HF system: 5.8GHz CW electric wave,ISM band
Detection angle: 360°(Ceiling installation),
1m-3m-6m-11m (radii.) (adjustable)(Ceiling installation)
25m Max. (adjustable)(Wall installation)
Time setting: 8sec-1min-5min-12min, (adjustable)
Power consumption: approx.0.5W
It can be defined in the range of 10~1000 LUX. To set the switch to ON is “1”, to OFF is “2”. Read through the right shown the corresponding table of the switch position to the light-control value.
It can be defined from 8 seconds to 12minute. Any movement detected before this time elapse will re-start the timer. It is recommended to select the shortest time for adjusting the detection range and for performing the walk test. To set the switch to ON is “1”, to OFF is “2”. Read through the right shown the corresponding table of the switch position to the delay time.
(3)Detection range setting (sensitivity)
Detection range is the term used to describe the radii of the roughly circle casting on the ground when installed at the height of 2.5 m. To set the switch to ON is “1”, to OFF is “2”. Read through the right shown the corresponding table of the switch position to the detection range.
Setting manner two:Remote control
ON: press ON, the load connected will keep working for 6 hours and then automatically turn to AUTO mode.
OFF: press OFF, the load connected will be off for 6 hours and then automatically turn to AUTO mode.
AUTO: press AUTO, sensor enters the auto-detecting mode, that is, when signal detected and the ambient light intensity is lower than the preset value, the load works.
|The load fails to work.||Light-illumination is set incorrectly.||Adjust the setting of the load.|
|The load is broken.||Change the load.|
|The power is off.||Turn the power on.|
|The load works all the time.||There is a continuous signal in the region of the detection.||Check the settings of the detection area.|
|The load works when there is no motion signal detected.||The lamp isn't installed well so that sensor fails to detect reliable signals.||Re-adjust the installation place.|
|Moving signal is detected by the sensor (movement behind the wall, the movement of small objects, etc.)||Check the settings of the detection area.|
|The load fails to work when there is motion signal detected.||The motion speed is too fast or the defined detection area is too small.||Check the settings of the detection area.|