Infrared Motion Sensor PD-PIR200N instruction
The Ceiling Occupancy Motion Sensor Detector Lamp Switch is a new saving-energy switch, it adopts good sensitivity detector, integrated circuit and SMT. It gathers automatism, convenient safe, saving-energy and practical functions. One detector inside compose a wide range detection field, it utilizes the infrared energy from human as control-signal source, it can start the load at once when one enters detection field. It can identify day and night automatically. It is easy to install and used widely, possessing the functions of power show and detecting show.
Identify day and night automatically. Can adjust light-control according to your desire: when turn to SUN (max), it will work in the daytime and at night. When turn to MOON (min), it will only work under less than 3LUX circumstance. As for Adjustment, please refer to testing way.
Detection range can be set according to installation position and detection field.
The detection show: the LED will flash two times per second when receiving the signal.
Time setting is added continually: when it receives the second induction signal after the first inductor, it will compute time once more on the rest of the first time setting basic. (Set time)
Time setting adjustment: it can be set according to your desire. The minimum is 8±3 sec; the maximum is 7±2min.
Power source: 220-240VAC
Power frequency: 50Hz
Rated load: 1200W Max.tungsten
Time setting: min: 8±3sec max: 7±2min (adjustable)
Detection angle: 360o
Detection range(22°C): 8m Max.(dia.) (adjustable)
Light-control: <3LUX-daylight (adjustable)
Working temperature: -10°C~+40°C
Power consumption: 0.45W (static 0.1W)
Installation height: 2.5~3.5m
Detection motion speed: 0.6-1.5m/s
Working humidity: <93%RH
ATTENTION: When use this product, please adjust the sensitivity to an appropriate position you need, please do not adjust the sensitivity to maximum, to avoid the product does not work normally caused by wrong motion.Because the sensitivity is too high easily detect the wrong motion by wind blowing leaves & curtains, small animals, and the wrong motion by interference of power grid & electrical equipment. All those lead the product does not work normally !
When the product does not work normally, please try to lower the sensitivity appropriately, and then test it.
Should be installed by electrician or experienced man.
Avoid installing it on the unrest objects.
There shouldn’t be hindrance and moving object in front of the detection window effecting detection. ?Avoid installing it near air temperature alteration zones such as air condition, central heating, etc.
Considering your safety, please don’t open the cover when you find the hitch after installation.
If there is difference between product and instruction, please refer to product mainly.
Some problem and solved way
The load don’t work:
a.Please check the power and load connect is correct.
b.Check if the load is good.
c.Check if the working light corresponds to the light-control.
The sensitivity is poor:
a.Please check if there is hinder in front of the detection window to effect receiving the signals.
b.Please check if the ambient temperature is too high.
c.Please check if the signals source is in the detection fields.
d.Please check if the installation height corresponds to the height showed in the instruction.
e.Please check if the moving orientation is correct.
The sensor can’t shut the load automatically:
a. Check if there are continual signals in the detection fields.
b. Check if the time setting is set to the longest.
c. Check if the power corresponds to the instruction.
d. Check if the temperature change obviously nears the sensor, such as air condition or central heating etc.
● When used in different environments, please do not to adjust the sensitivity to the highest. Because that could easily lead to malfunction.
● Please confirm with prefessional installation.
● Please cut off power supply before installation and removal operations.
● Make sure that you have cut off the power for safety purposes.
● Improper operation caused losses, the manufacturer does not undertake any responsibility.
We are committed to promoting the product quality and reliability, however, all the electroniccomponents have certain probabilities to become ineffective, which will cause some troubles.When designing, we have paid attention to redundant designs and adopted safety quota to avoid any troubles.
This instruction, without our permission, should not be copied for any other purposes.
Turn LUX knob anti-clockwise to the maximum (SUN). Turn time knob clockwise to the minimum.
At the time of your switching on the power, the load doesn’t work. After 5-10 sec, the load works and the LED flashes twice every second. Under the no induction conditions, the load should stop working within 5-30 sec, and the LED should goes out ;
If make it sense again 5-10 seconds later after it goes out, load should work and the flashing speed is two times per second, then load will stop working within 5-15 seconds.
Turns LUX knob clockwise to the minimum. If it is tested under the circumstance below 3LUX, load should not work after induction load stop working; but if you cover the detection window with opaque objects (towel etc), the load works. Under the condition of no induction signals, the load should stop working within 5-15 sec.
Hot Tags: Ceiling Occupancy Motion Sensor Detector Lamp Switch, China, Manufacturers, Suppliers, Factory, Wholesale, Customized